# Design Formulas for the Leakage Inductance of Toroidal

0 of 0
100% ## Transcript Of Design Formulas for the Leakage Inductance of Toroidal

IEEE TRANSACTIONS ON POWER DELIVERY, VOL. 26, NO. 4, OCTOBER 2011

2197

Design Formulas for the Leakage Inductance of Toroidal Distribution Transformers
Iván Hernández, Student Member, IEEE, Francisco de León, Senior Member, IEEE, and Pablo Gómez, Member, IEEE

Abstract—In this paper, design formulas for the calculation of the leakage inductance of toroidal transformers are presented. The formulas are obtained from the analytical integration of the stored energy. The formulas are sufﬁciently simple and accurate to be introduced in the loop of a design program avoiding expensive ﬁnite element simulations. It is found that toroidal transformers naturally produce the minimum leakage inductance possible for medium-voltage power transformers. To limit the short-circuit currents in power and distribution systems, a larger than the minimum leakage inductance is often required. This paper presents two methodologies to increase the leakage inductance of toroidal distribution transformers: selectively enlarging the inter-winding spacing and inserting a piece of ferromagnetic material in the leakage ﬂux region between the windings. Extensive validation with 2D and 3D ﬁnite element simulations is performed. Additionally, experimental veriﬁcation of both formulas and numerical simulations was carried out comparing the calculations against measurements on prototypes.
Index Terms—Finite-element method, leakage inductance, toroidal transformers.
I. INTRODUCTION
F ARADAY in 1831 built the ﬁrst transformer in a toroidal core ; see Fig. 1. The ﬁrst industrial grade transformer, the one of the Ganz factory in Budapest of 1885, was also wound on a toroidal core  (see Fig. 2). Currently, however, toroidal transformers are not widely used for transmission and distribution of bulk power. There are two basic arrangements used to build the iron cores of medium and large transformers –: 1) core type where the cores are assembled by stacking laminations and sliding premade windings and 2) shell type, where a continuously wound core is cut and wrapped around the windings a few laminations at a time. In both arrangements, the ﬁnished core has air gaps that increase the magnetizing current and the no-load losses.
Toroidal transformers have found modern applications in the low-voltage low power of many power supplies for electronic
Manuscript received June 17, 2010; revised March 08, 2011; accepted May 10, 2011. Date of publication June 28, 2011; date of current version October 07, 2011. This work was supported by the U.S. Deparment of Energy under Grant DEOE0000072. Paper no. TPWRD-00457-2010.
I. Hernández is with the CINVESTAV Guadalajara, Jalisco 45015, México (e-mail: [email protected]).
F. de León is with the Department of Electrical and Computer Engineering of Polytechnic Institute of New York University, Brooklyn, NY 11201 USA (e-mail: [email protected]).
P. Gómez is with the Electrical Engineering Department, SEPI-ESIME Zacatenco, Instituto Politécnico Nacional (IPN), Mexico City 07738, Mexico (e-mail: [email protected]).
Color versions of one or more of the ﬁgures in this paper are available online at http://ieeexplore.ieee.org.
Digital Object Identiﬁer 10.1109/TPWRD.2011.2157536

Fig. 1. Photo of Faraday’s original transformer .
equipment, avionics, and audio systems , . A very limited amount of published material exists in the IEEE related to toroidal transformers for power conversion applications; see –. There are not any papers published related to mid- or high-voltage toroidal transformers intended for use at utility voltages. Transformers wound on nongapped toroidal cores using grain-oriented silicon (Si) steel are more efﬁcient, smaller, cooler, and emit reduced acoustic and electromagnetic noise when compared with standard transformer constructions. To extrapolate these advantages to distribution transformers, an effort is being made now, as part of a U.S. Department of Energy funded project, to produce toroidal transformers suitable for power distribution system applications. Although toroidal transformers have many advantages over traditional constructions, there are also a few disadvantages that need to be overcome before widespread adoption of toroidal transformers is possible. Most important, there is no published experience in the industry when it comes to designing and building toroidal transformers suitable for operation at medium and high voltage. Unresolved issues with toroidal transformer design and manufacturing include matching the leakage impedance speciﬁcation, limiting inrush currents, designing and constructing to withstand short-circuit currents, the study of electromagnetic transients (impulse test), design for cost optimization, and the ability to pass industry-standard acceptance tests. This paper is part of a series describing the solutions to those issues via electromagnetic design, design veriﬁcation, building prototypes, performance veriﬁcation, and observation of prototypes installed on a utility distribution system. In low-voltage, low-power applications, the leakage inductance can be minimized using planar transformers or highly interleaved windings. For high-power, medium-voltage transformers, the leakage inductance of toroids is the minimum achievable. The reason for this is the closed concentric geometry. The ﬁrst winding

2198

IEEE TRANSACTIONS ON POWER DELIVERY, VOL. 26, NO. 4, OCTOBER 2011

Fig. 2. Drawing of the Ganz factory transformer .
completely covers the core and subsequent windings cover the internal windings. There are no yokes where the ﬂux could escape to the air. Therefore, the electromagnetic coupling is maximized, while the leakage and stray ﬁelds are minimized. The small regulation characteristic that can be obtained with toroidal transformers by minimizing the leakage impedance is desirable for many applications. However, in a power system, the transformers’ leakage impedance is one of the important components used for limiting the short-circuit currents. Consequently, a larger than natural leakage inductance may be required for a toroidal transformer.
A contribution of this paper is to propose two methods to increase the leakage inductance of toroidal transformers: 1) enlarging the spacing between primary and secondary windings and 2) inserting high permeability materials between primary and secondary windings.
Another contribution of this paper is the derivation of equations suitable for implementation in a design program for the calculation of the leakage inductance of toroidal transformers. The ﬁnal expressions are numerically very efﬁcient and sufﬁciently accurate for practical design work. Validation against a large number of ﬁnite-element simulations in 2-D and 3-D covering distribution transformers of 25, 37.5, 50, and 75 kVA was performed.

II. DISTRIBUTION OF THE LEAKAGE FIELD

Coherent with the standardized method to measure the

leakage inductance, for its computation, one must simulate

the short-circuit test. In other words, force

,

eliminating the magnetizing current. Fig. 3(a) shows an ax-

isymmetric view of the distribution of the magnetic-ﬁeld

strength in a toroidal transformer during a short-circuit test.

Five distinct sections having different ﬁeld distribution charac-

teristics can be identiﬁed:

1) vertical internal part of the windings;

2) vertical external part of the windings;

3) top and bottom horizontal parts;

4) internal corners;

Fig. 3. Distribution of the magnetic-ﬁeld strength in the toroidal transformer: (a) Axisymmetric view. (b) Radial distribution of the magnetic ﬁeld on the vertical sections. (c) Magnetic-ﬁeld strength on the horizontal sections at three positions. (d) Radial variation of the ﬁeld at the insulation of the horizontal parts.
5) external corners. One can distinguish three subregions: two corresponding to the two windings and one for the insulation between them

HERNÁNDEZ et al.: DESIGN FORMULAS FOR LEAKAGE INDUCTANCE

2199

in each of the ﬁve regions. Fig. 3(b) shows the magnetic-ﬁeld strength on the vertical part of the windings along the line A-A’. One can see that the magnetic ﬂux in the vertical direction almost follows the trapezoidal distribution characteristic of traditional transformer designs. In addition, note that the magnetic-ﬁeld strength is independent of the vertical position.
The top and bottom sections, regions 3 of Fig. 3(a), have identical magnetic-ﬁeld distributions as shown in Fig. 3(c). Note, however, that while the vertical variation of the ﬁeld follows the trapezoidal distribution, the ﬁeld strength reduces in inverse proportion with the distance to the axis; see Fig. 3(d).
The leakage inductance of the toroidal transformer can be obtained through closed-form volumetric integration of the distribution of the magnetic energy stored as follows:

(1)

It is noticed that the different components of the leakage inductance can be obtained by analyzing the distribution of the magnetic-ﬁeld strength at each section. Two main assumptions are made regarding the distribution of the magnetic-ﬁeld strength as follows.
• The radial distribution (around the toroidal circumference) is considered constant (axisymmetric model).
• The distribution of transversal to the windings is considered as follows: it rises linearly in one winding, varies inversely with in the insulation between windings, and decays linearly in the opposite winding. This type of distribution can be described by the following expression:
(2)

Fig. 4. Main geometrical data of a toroidal distribution transformer.
A. Vertical Parts (Sections I and II) In Sections I and II (internal and external vertical parts of the
winding, respectively), the peak values of are shown in Fig. 4. These peaks can be computed from Ampere’s Law as follows:

where

is the maximum value of the magnetic-ﬁeld

strength; in this paper,

is identiﬁed in ﬁve ways de-

pending on the section being considered: , (internal

and external vertical sections of the winding, respectively);

, correspond to the internal and external spaces

between the windings (i.e., insulation); and

(hori-

zontal sections of the winding); while , , and corre-

spond to the thickness of the high-voltage (HV) winding,

low-voltage (LV) winding, and interwinding insulation, re-

spectively (as indicated in Fig. 4).

III. DESIGN FORMULAS FOR THE LEAKAGE INDUCTANCE
From the identiﬁcation of the ﬁve different sections, the total leakage inductance of the winding can be computed as

(3)

where

corresponds to the leakage inductance component

of the th section of the winding (for 1, 2, 3, 4, 5). Ex-

pressions for each section will be obtained as shown (using the

Cartesian coordinate system).

(4a)
(4b)
where is the number of turns of the exciting winding; is the current; and are the internal radii of the insulation for the vertical regions 1 and 2, respectively; and and are the internal radii of the external winding for regions 1 and 2. The reduction of the magnetic-ﬁeld strength between the windings, from to as is considered. When the insulation between windings is small, we can assume that has a trapezoidal distribution. In , we have computed that 1 mm of insulation between windings is enough to produce transformers class 95-kV BIL.
Combining (1) and (4), the leakage inductance of Section I is computed from

2200

IEEE TRANSACTIONS ON POWER DELIVERY, VOL. 26, NO. 4, OCTOBER 2011

(5)

where is the height of the toroid; , , and

cor-

respond to mean radii of the HV winding, insulation, and LV

winding, respectively, and computed, in general, as

(6)

Substituting (4a) into (5) and performing the integral, one obtains

(7)
The leakage inductance for Section II is computed in a similar manner as

(8)

The radial distance on the -axis can take values from

, where and are the internal and external radii

of the toroid, respectively. Thus, the leakage inductance of the

horizontal sections is obtained from (10), shown at the bottom

of the page.

is the mean radius of the horizontal sections,

given by

(11)
Substituting (9) in (10), performing the integral, and using (11), we obtain

(12)

C. Corners (Sections IV and V)
For the corners, the same peak values for the magnetic ﬁeld deﬁned for the internal and external vertical parts are considered as given by (4a) and (4b). The trapezoidal distribution of is around the corner, so it was necessary to perform the integral around its periphery denoted by (from 0 to ); the leakage inductance for the internal corners is obtained from (13), shown at the bottom of the page.
Solving (13), it follows that:

B. Horizontal Parts (Section III)
The top and bottom parts have the same ﬁeld distribution; see Fig. 3(c). The value of at the interwinding insulation is computed from Ampere’s Law as follows:

where

(9)

(14)
(15a) (15b) (15c)

(10)

(13)

HERNÁNDEZ et al.: DESIGN FORMULAS FOR LEAKAGE INDUCTANCE
TABLE I COEFFICIENTS FOR THE DIFFERENT COMPONENTS OF THE LEAKAGE
INDUCTANCE FORMULA (17)

2201
TABLE II DESIGN PARAMETERS FOR SINGLE-PHASE TOROIDAL TRANSFORMERS

Similarly, the leakage inductance for the external corners is computed as

TABLE III PARAMETERS COMPUTED FOR SINGLE-PHASE TOROIDAL TRANSFORMERS

(16)

D. Generalized Expression
One can appreciate that (7), (8), (12), (14), and (16) have a similar form. Therefore, a generalized expression for the calculation of the contribution to the leakage inductance of each section can be obtained as follows:
(17)
The coefﬁcients for the different sections are given in Table I. The total leakage inductance is computed from (3).

TABLE IV IMPEDANCE DATA FOR THE SINGLE-PHASE TRANSFORMERS FROM

IV. TEST CASES
Table II shows the design parameters of a set of toroidal distribution transformers used to demonstrate the applicability of the methods and the accuracy of the formulas. We have selected the standardized sizes for distribution transformers per . The leakage inductance reference values have been computed with 3-D ﬁnite-element simulations using the commercially available software (COMSOL Multiphysics) .
The FEM simulations performed solve for the magnetostatic formulation. All materials are considered as being isotropic; we used copper windings and electrical steel M4 (0.28 mm) for the main core considering its B-H curve as provided by the manufacturer.
In the simulations, the toroid was enclosed by a tank represented by a rectangle in the axisymmetric 2-D case and by a cylinder in the 3-D case. Magnetic insulation was applied to the boundaries of the tank walls. For the 2-D simulations, about 40 000 triangular elements were necessary, consuming about 2 GB of random-access memory (RAM). For the 3-D simulations, about 400 000 tetrahedrons were employed, consuming 9-GB

RAM. The axisymmetric 2-D and 3-D simulation results were almost identical. Therefore, we conclude, as expected from a symmetrical construction, that to compute the leakage inductance, 2-D axisymmetric modeling is sufﬁcient.
Table III shows the values of leakage inductances and reactances in percent that can be achieved with toroidal transformers. The inductive values are referred to the HV winding. From Table III, one can appreciate that the results are in good agreement, with maximum differences of 3%.
Table IV shows the leakage impedance values recommended by the IEEE Standard 242-1986  for the calculation of shortcircuit currents. It can be noticed that the reactance in percent of toroidal transformers may be substantially smaller than that of conventional transformers. Therefore, larger short-circuit currents can be expected. Although small regulation is, in general, a desirable characteristic for a transformer, for some applications, the larger short-circuit currents that occur may not be acceptable. In the next section, two methods to increase the leakage inductance are proposed.

2202

IEEE TRANSACTIONS ON POWER DELIVERY, VOL. 26, NO. 4, OCTOBER 2011

V. METHODOLOGIES FOR INCREASING THE LEAKAGE INDUCTANCE OF TOROIDAL TRANSFORMERS

A. Increasing Interwinding Spacing
One can perceive from Tables III and IV that the leakage inductance of a 25-kVA toroidal transformer may be as small as half of what is speciﬁed in the standard .
From the expressions obtained in Section III and their analogy with the technology of traditional transformer constructions, it can be inferred that increasing the spacing between windings will increase the leakage inductance. This is a technique known to designers and manufacturers of traditional transformer constructions. It is possible to identify in (7), (8), (12), (14) and (16) the middle term as the inductance corresponding to leakage ﬂux in the insulation (or air). To build toroidal transformers, the internal space at the center of the toroid must be large enough for the winding machine to pass. Therefore, only the top, bottom, and external regions can be used in practice to increase the leakage path. Furthermore, when considering manufacturing aspects, the most suitable region to increase the interwinding space is the external part (region 2 of Fig. 3). Therefore, in this paper, only the external interwinding space of the toroidal transformer is used to increase the leakage inductance; see Fig. 5. Taking this into consideration, the leakage inductance for the vertical external component of the winding (region 2), given by (8), is modiﬁed as follows:

Fig. 5. Enlarging the external vertical interwinding space to augment the leakage inductance.

(18) where is the increased space in the interwinding region. The leakage inductance corresponding to the horizontal components of the winding (regions 3 and 4), given by (12), is also modiﬁed, resulting in the following expression:

(19)

Fig. 6(a) shows the variation of the leakage inductance with the interwinding space for the four transformer ratings under study. One can appreciate that increasing the interwinding spacing increases the leakage inductance by a relatively modest amount. The values have been normalized with respect to the minimum interwinding space needed for insulation purposes (1 mm).
The results from the formulas of this paper against FEM are compared in Fig. 6(b) for the transformer 25 kVA. One can appreciate a very good match between the formulas and FEM (differences of about 4%).
As a conclusion of this section, one can observe that the technique of increasing interwinding spacing is effective when relatively small increments of the leakage inductance are needed. However, when large increments are sought, a different technique is necessary. Furthermore, adding larger spaces than required for insulation purposes adds cost and weight to the transformer. The most signiﬁcant negative consequence is that the

Fig. 6. Variation of the leakage inductance: (a) Calculated for four different ratings of toroidal distribution transformers. (b) Comparison of the analytical results with FEM for a 25-kVA toroidal transformer.
external winding has a longer mean length (adding production cost and operation losses).
B. Ferromagnetic Inserts The second technique proposed in this paper to increase the
leakage inductance is to augment the permeability of the material in the leakage region. By inserting ferromagnetic material

HERNÁNDEZ et al.: DESIGN FORMULAS FOR LEAKAGE INDUCTANCE

2203

Fig. 7. Illustration of adding ferromagnetic inserts between windings to increase the leakage inductance.
between the windings, we can dramatically magnify the leakage inductance without a noticeable increase in the transformer size.
The underlying idea is to install a thin core in the interwinding region on the external face; see Fig. 7. This produces an enlargement of the leakage inductance component corresponding to such a region. Equation (8) is modiﬁed as

(20) where is the thickness of the region occupied by the ferromagnetic material and is its relative permeability. The leakage inductance for the horizontal components of the winding is modiﬁed in a similar fashion as (12), yielding:

Fig. 8. Increase of the leakage inductance. (a) Inserting four different ferromagnetic materials between the windings. (b) Comparison of results between formulas and FEM for the 25-kVA transformer.

(21)
By adding material with high relative permeability , the value of the leakage inductance can be magniﬁed by a large factor. When using this technique, care must be taken to avoid saturation of the thin core placed between the windings.
Different ferromagnetic materials  were considered for the simulations performed to validate this technique. Fig. 8(a) shows the variation of leakage inductance with thickness for materials with different permeability. The plot is given in per unit (p.u.), normalized to the minimum insulation space and permeability of air . A comparison between the results of the formulation and FEM is shown in Fig. 8(b). One can notice that the differences are very small.
VI. EXPERIMENTAL VERIFICATION
With the purpose of validating the formulas proposed in this paper and the FEM simulations, a set of prototypes was built with ratings of 150 VA, 300 VA, 1 kVA, 2 kVA, and 4 kVA. The leakage inductance was measured by applying two methods: 1) using the standardized short-circuit (SC) test and 2) using

an RLC meter (7600 Precision LCR meter) available in the lab. This meter uses an ac signal of 2 V at 60 Hz and it gives the equivalent series R-L circuit of the transformer directly. In all cases, the secondary windings of the transformers are shorted and the primary windings are connected to the source.
Table V shows the comparison of the measurements on the ﬁve prototypes against ﬁnite elements simulations and the formulas of this paper. One can appreciate that for most cases, the results are very close between the four different methods (SC, RLC meter, FEM, and formulas). The differences are, in general, less than 3%. The sole exception is the SC measurement of the 300-VA double-core transformer with 8.47% difference. This transformer was opened and unwound. We found that the external (powder) core was fractured. Therefore, the effective permeability of this core was reduced by the irregular (unintended) air gap, explaining why the measurements gave a slightly smaller leakage inductance when compared with FEM and the formulas.
These experiments not only corroborate the accuracy of the calculation method proposed in this paper, but also conﬁrm the applicability of ferromagnetic inserts to increase the leakage inductance when large leakage is necessary.

2204

IEEE TRANSACTIONS ON POWER DELIVERY, VOL. 26, NO. 4, OCTOBER 2011

TABLE V LEAKAGE INDUCTANCE MEASURED AND COMPUTED
FOR SINGLE-PHASE TOROIDAL TRANSFORMERS
VII. CONCLUSION Formulas suitable for a design program for the calculation of the leakage inductance of toroidal transformers have been developed. From the observation of the distribution of the magnetic ﬂux in the leakage region, precise expressions have been derived for the magnetic-ﬁeld strength. The leakage inductance is obtained by the analytical integration of the total energy stored in the magnetic ﬁeld. The formulas have been compared against 2-D and 3-D ﬁnite-element simulations, yielding very good results; with differences under 4%. Two methodologies to augment the leakage inductance of toroidal transformers have been proposed. We have investigated increasing the interwinding spacing and the addition of a ferromagnetic core in the leakage region. Increasing the interwinding spacing is effective for up to a 1.5-p.u. increment of the leakage inductance at the cost of increasing the mean length of the external winding. The addition of a ferromagnetic core between the windings offers an inexpensive alternative to augment the leakage inductance. This technique can be conveniently used to increase the leakage inductance of several orders of magnitude. The accuracy of the formulas and the applicability of the methods to increase the leakage inductance have been corroborated experimentally for a set of prototypes of various sizes.
ACKNOWLEDGMENT The authors would like to thank U. Poulsen of Bridgeport Magnetics for his fast response and expertise building the prototypes. The authors would also like to thank C. Prabhu and N. Augustine, M.Sc. students of Polytechnic Institute of New York University, for performing the leakage inductance tests to the prototypes. In addition, the authors would like to thank the reviewers for their sharp comments that have added value to this paper.
REFERENCES
 F. A. Furfari and J. W. Coltman, “The transformer,” IEEE Ind. Appl. Mag., vol. 8, no. 1, pp. 8–15, Jan./Feb. 2002.
 S. Jeszensky, “History of transformers,” IEEE Power Eng. Rev., vol. 16, no. 12, pp. 9–12, Dec. 1996.
 J. H. Harlow, Electric Power Transformer Engineering, 2nd ed. Boca Raton, FL: CRC, 2007.
 S. V. Kulkarni and S. A. Khaparde, Transformer Engineering Design and Practice. New York: Marcel Dekker, 2004.

 R. M. V. Del, B. Poulin, P. T. Feghali, D. M. Shah, and R. Ahuja, Transformer Design Principles—With Application to Core-Form Power Transformers. New York: Gordon and Breach, 2001.
 M. Heathcote, J & P Transformer Book, 12th ed. London, U.K.: Butterworth–Heinemann, 1998.
 M. van der Veen, Modern High-end Valve Ampliﬁers: Based on Toroidal Output Transformers. Dorchester, U.K.: Elektor Electronics Publishing, 1999.
 A. A. Halacsy, “Reactance and eddy current loss in toroidal transformatoric devices-II,” AIEE Trans. Power App. Syst, vol. 81, no. 3, pp. 1017–1019, Apr. 1962.
 R. Prieto, J. A. Cobos, V. Bataller, O. Garcia, and J. Uceda, “Study of toroidal transformers by means of 2D approaches,” presented at the IEEE 28th Ann. Power Electron. Specialists Conf., St. Louis, MO, Jun. 22–27, 1997.
 R. Prieto, V. Bataller, J. A. Cobos, and J. Uceda, “Inﬂuence of the winding strategy in toroidal transformers,” in Proc. IEEE 24th Annu. Conf. Ind. Electron. Soc., Sep. 1998, vol. 1, pp. 359–364.
 J. P. Myers, K. A. Weaver, W. R. Wieserman, and U. Poulsen, “O cores—A new approach,” in Proc. Elect. Insul. Conf. Elect. Manuf. Coil Winding Technol. Conf., Sep. 23–25, 2003, pp. 193–198.
 P. Gómez, F. d. León, and I. Hernández, “Impulse response analysis of toroidal core distribution transformers for dielectric design,” IEEE Trans. Power Del., vol. 26, no. 2, pp. 1231–1238, Apr. 2011.
 IEEE Recommended Practice for Protection and Coordination of Industrial and Commercial Power Systems, IEEE Std. 242-1986, Feb. 1986.
 “Comsol Multiphysics, AC/DC User’s Guid,” Comsol AB Group, 2006, pp. 1–156.
 A. Goldman, Handbook of Modern Ferromagnetic Materials. Norwell, MA: Kluwer, 1999, vol. I, pp. 64–135.
Iván Hernández (S’06) was born in Salamanca, Guanajuato, Mexico, in 1979. He received the B.Sc. degree in electrical engineering from the University of Guanajuato, Salamanca, Guanajuato, Mexico, in 2002, and the M.Sc. degree in electrical engineering from the CINVESTAV Guadalajara, Jalisco, Mexico, in 2005, where he is currently pursuing the Ph.D.degree.
From 2008 to 2010, he was on a study leave at the Polytechnic Institute of New York University, Brooklyn, NY. Previously, he was an Electrical Engineer Designer for two years with FMS Ingeniería, Guadalajara, Mexico. His research interests are numerical analysis applied to machine design and software simulation tools, particularly for electromagnetic ﬁelds.
Francisco de León (S’86–M’92–SM’02) was born in Mexico City, Mexico, in 1959. He received the B.Sc. and the M.Sc. degrees in electrical engineering from the National Polytechnic Institute, Mexico City, Mexico, in 1983 and 1986, respectively, and the Ph.D. degree from the University of Toronto, Toronto, ON, Canada, in 1992.
He has held several academic positions in Mexico and has worked for the Canadian electric industry. Currently, he is an Associate Professor at the Polytechnic Institute of New York University, Brooklyn, NY. His research interests include the analysis of power phenomena under nonsinusoidal conditions, the transient and steady-state analyses of power systems, the thermal rating of cables, and the calculation of electromagnetic ﬁelds applied to machine design and modeling.
Pablo Gómez (S’01–M’07) was born in Zapopan, México, in 1978. He received the B.Sc. degree in mechanical and electrical engineering from Universidad Autonoma de Coahuila, Mexico, in 1999, and the M.Sc. and Ph.D. degrees in electrical engineering from CINVESTAV, Guadalajara, Mexico, in 2002 and 2005, respectively.
Since 2005, he has been a Full-Time Professor with the Electrical Engineering Department, SEPI-ESIME Zacatenco, National Polytechnic Institute, Mexico City, Mexico. From 2008 to 2010, he was on a postdoctoral leave at the Polytechnic Institute of New York University, Brooklyn, NY. His research interests are modeling and simulation for electromagnetic transient analysis and electromagnetic compatibility.
Leakage InductanceWindingsFigToroidal TransformersPaper